|Power Rating||>22 kVA|
|Rating Compensation Current||30~600A|
|Filter Frequency||Greater than 97%|
The increasing use of modern power electronic apparatus (drives, uninterruptible power supplies, etc.) produces nonlinear current and thus loads the network with harmonics. The capacitance of the power capacitor forms a resonant circuit in conjunction with the feeding transformer. Experience shows that the self-resonant frequency of this circuit is typically between 250 and 500 Hz, i.e. in the region of the 5th and 7th harmonics. Typical loads requiring harmonic filtering include 6 pulse drives (AC / DC), 3 phase UPS, frequency converters.
|Minimum Order Quantity||1 Piece|
|Measuring Voltage Range||415 V / 440 V|
|Rated Frequency||50 Hz|
|Reactance Factor||5.67%, 7% and 14% (0.2% on request)|